MODEL PAW ULTRA
Make a bold statement with the PAW ULTRA series heater. Adding modern sophistication to our original Pic-A-Watt multi-watt steel fin heater with its sleek modern grill design, the ULTRA is ideal for upscale condominiums and luxury residences. King’s exclusive Pic-A-Watt steel fin element allows customers to select from a range of wattage options, tailoring the heater to an area’s specific heating requirements. Perfect for large living areas yet whisper quiet enough for bedrooms. The premium combination of an efficient high-mass steel element and whisper quiet squirrel cage blower, offers top of the class performance and years of trouble -free operation. Now That’s Smart!
Tailored Comfort For Your Space
Perfect for large living areas yet whisper quiet enough for bedrooms. Featuring King’s exclusive Pic-A-Watt element. Customers can select from a range of wattage options, tailoring the heater to an area’s specific heating needs.
Now That’s Smart!
Safe Comfort For Families
Patented Smart Limit Protection (U.S. Patent #6,748,163 B2) automatically shuts power off to the heater in an abnormal event and must be manually reset for safety.
The Original Pic-A-Wattage Element® Multi-Wattage Element
King’s exclusive Pic-A-Watt element means the heater can easily be tailored to a room’s specific heating requirements. For smaller areas, choose a lower wattage to efficiently heat the room. For larger rooms, choose a higher wattage and maximize comfort. It’s easy as unplugging a wire to select the wattage during installation.
|MODEL||UPC||VOLTS||WATTS||AMPS||SHIP WEIGHT lbs|
Contractor shall supply and install PAW Ultra Series in-wall forced-air electric heaters manufactured by King Electrical Mfg. Company, of the wattage and voltage as indicated on the plans.
Ratings: Heaters shall be available in wattages of 250 to 2,250 at 120, 208, 240, or 277 Volts.
Blower and Motor: A whisper quiet tangential blower, delivering 75 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater.
Elements: Element assemblies shall consist of three steel sheathed heating tubes in a furnace-brazed, plate-finned, block design. Each sheathed tube shall contain coiled Ni-Chrome wire embedded in an insulator of Magnesium Oxide. The element assembly shall provide up to seven (7) possible wattage configurations available for selection during field installation. The use of external resistors, diodes, or other weak links to obtain multiple wattages will not be acceptable.
Thermal Overload: Heaters shall be equipped with King’s patented thermal overload Smart Limit Protection®, which disconnects elements and motor in the event normal operating temperatures are exceeded. If thermal overload trips due to abnormal operating temperatures, thermal overload shall remain open until manually reset by turning the heater off for 15 minutes. Automatic reset of thermal overloads, which allow the element to continue to cycle under abnormal conditions, will not be accepted.
Grill: The grill shall be a louvered with multiple linear steel bars secured to a steel back plate, with rounded sides to prevent snags with other materials. The grill shall be epoxy powder-coated in white or almond.
Wall Can: The wall can shall be 20 gauge electro-galvanized steel and shall contain a minimum of three (3) knockouts. The wall can shall have a depth gauge indicator, and a factory installed, insulated and stranded copper ground-wire. Minimum 4”clearance to floors and 6”sidewalls. Zero clearance to combustibles in the wall.
Approvals: cULus (E41422)