Model CLEAR AIR MAU
The King Clear Air Make-Up Air Unit is designed to “make up” the air in your interior space that has been removed due to process exhaust fans. The building ventilation and the make-up air system work together to ensure the building pressure is maintained, while eliminating temperature fluctuations and a number of air quality issues. Clear Air MAU preheats the incoming fresh air at the lowest cost, thus continuously providing comfortable ventilation throughout the building. Featuring an energy efficient ECM motor, the Clear Air combines a fan driven fully modulating electric heating unit with a fresh air relay logic control circuit providing an extremely versatile all-in-one packaged unit. It is designed to work with HVAC equipment to provide indoor air quality into a return side or supply side of the ductwork system or alternatively directly into the building space.
- Packaged, All-In-One Make Up Air Solution
- 700-1770 CFM @ 0.2” Static Pressure
- Proportional Thermostat For Fully Modulating Electric Heat
- Wide Range of Air of CFM, Temperature Rise & Static Pressure Configurations
- Energy Efficient ECM Motor with 5 Torque Taps
- Available in 208/240V/480V - Single & Three Phase
- Included Duct Sensor For Precise Set Points
- Automatic Damper Control
- Current Transformer Technology For Full Interlock With Exhaust Systems
- Relay Logic Control Circuit Enabling Control of Other Make-Up Air Components (Damper, Exhaust Fans, Outside Thermostat & Humidistat, Etc).
- Horizontal or Vertical Installation
- Compact Footprint
- Replaceable Air Filter (1" or 2" thick)
- Shown with MAUFH Filter Housing (Required and Sold Separately)
- Proudly Made in USA
- 3-Year Limited Warranty
Constant Comfortable Ventilation
Today’s airtight homes and offices beg for fresh air. Stale and humid air must be replaced by fresh air. During winter, the incoming fresh air is at too low a temperature to be comfortable and the Clear Air Fresh Air Series preheats the incoming air to your preset temperature.
Now That’s Smart!
The Relay Logic Control Circuit Means It Is Easily Tailored To Any Application
Relay logic control circuit enabling control of other make-up air components (damper, exhaust fans, outside thermostat and humidistat, etc).
Now That’s Smart!
ENERGY SAVINGS meets MAXIMUM FRESH AIR
The Clear Air Fresh Air features a state of the art electronically controlled motor for Maximum Energy Savings and Maximum Fresh Air.
Now That’s Smart!
Contractor shall furnish and install King Clear Air Make-Up Air Unit manufactured by King Electrical Manufacturing.
Motor: Direct drive high efficiency, thermally protected, permanently lubricated ECM motor, no belts to adjust or maintain.
Motor Terminal: Clear Air shall have a 5-point terminal block to easily field adjust the motor torque setting of the ECM motor.
Modulating Heat: 100% fully modulating heating control through Solid State Relay (SSR) technology. The SSR relays shall be mounted in the blower compartment to allow the free flow of incoming air to cool the heat sinks.
Thermostat: Clear Air shall be controlled by an electronic proportional thermostat using a 0 to 10VDC of 4 to 20ma signal. The inbuilt thermostat
can be removed and relocated to room and used as a wall mounted thermostat.
Duct Sensor: Clear Air shall be provided with a field installed duct sensor, type 2 NTC thermistor, 10K ohms.
Heating Elements: Quick heating, long life Ni-Chrome elements supported by a steel frame and insulated with ceramic holders.
LV Terminal Block: All low voltage wires are terminated at a 14-point block with factory side quick connects and field side screw terminals.
Control Circuit: Clear Air shall have a relay logic control circuit providing a dedicated 24V power supply that is switched to activate external devices such as:
a damper, exhaust fan, etc.
Lockout Circuit: Clear Air shall have a lockout circuit for auxiliary devices such as an outside thermostat or humidistat to prevent the Clear Air system from turning on
unless predetermined conditions are met.
Overcurrent Protection: Clear Air shall have a 24V high temperature limit circuit wired in series to protect each individual heating element. In addition, it shall have one electrically held manual limit monitoring the condition of entire unit. If tripped, this limit must be manually reset by shutting off the power, waiting several minutes and then turning the power back on. This provides an extra level of overheating protection to the unit.
Enclosure: Clear Air shall be constructed from 20GA electrogalvanized sheet metal of welded construction and finished with a corrosion resistant gray finished. Unpainted sheet steel is not acceptable. Access to the wiring compartment shall be from the side for easy wiring and maintenance. The unit shall have welded brackets with 6 – 3/8” weld nuts for sturdy mounting either vertically or horizontally. Provide both Line voltage and Low voltage knockouts to speed contractor installation. Provide knockouts for an optional disconnect.
Blower: Centrifugal dual inlet blower shall be used, axial fans not permitted. Blower shall be rigidly mounted to the enclosure with internal welded mounting brackets.
Optional Disconnect: The unit shall have the option to mount an internal Supply Power Disconnect.
Approvals: UL: Clear Air shall be Underwriters Laboratory (UL) approved and labeled.